November 17, 2020
A postponed UPS replacement due to the Corona Virus lockdown finally received approval to proceed.
The systems were installed without interrupting power to the load due to the fact that the UPS’s were originally installed with external manual bypass switches.
November 11, 2020
Following the Covid-19 “lockdown”, many companies are realising that now is the perfect time (before staff return to offices) to perform planned preventative maintenance visits
October 28, 2020
Visited a sight the other day to maintain 4 x parallel 40KVA UPS systems.
The UPS’s are mounted on a plinth with no room to pull them forward even onto a wheeled dolly.
In order to get into these UPS’s for repair or to replace batteries you have to disconnect and take one system out of the room, which provides enough side space to work on the others. Nightmare!
October 14, 2020
When the original batteries on a UPS needed replacing, the customers load had reduced (over the years) to about 10% of the UPS capacity.
So rather than specify 10 minutes back-up at full UPS load, it was decided that 10 minutes at the lighter load was all that was needed.
The UPS was de-rated via the set-up software and battery fuse sizing was reduced.
New smaller battery rack installed with feet spacing to mimic the previous rack
July 22, 2020
A recent request to inspect and evaluate a UPS installation at a high street store uncovered the fact that the UPS was shut down with batteries disconnected. All equipment normally supported by a UPS (tills, security etc.) was just being powered from normal mains power
May 13, 2020
Recently installed a 10KVA Sentryum UPS to replace a competitors old defective system. As the original installation incorporated an external manual bypass switch, the replacement UPS was installed and switched into service without the need to interrupt the power.
This is the third generation of transformerless ON LINE UPS. The 10-20 kVA Sentryum rewrites the concept of flexible power by offering a choice of three compact cabinet sizes to suit the needs of any small datacentre or mission-critical application.
Enhanced overload and short circuit capacity guarantee maximum availability. Incorporating a 5-inch colour touchscreen display and intuitive LED status indicator that automatically changes colour based on the UPS’s current operating state.
April 15, 2020
An old 6KVA UPS was replaced with a new unity power factor “SDU” (Sentinel Dual) UPS.
As the original UPS was installed with an external manual bypass switch (EMBS) there was no interruption to server power and the whole was performed seamlessly.
March 11, 2020
UPS upgrade to a new Multi Sentry from an old Multi Dialog together with new batteries
February 24, 2020
60kva UPS with 35 minutes batteries positioned and commissioned in Docklands
February 12, 2020
Parallel 12KVA UPS systems installed at a travel company’s new head office to protect their data room. Each UPS has it’s own batteries and an overall external manual bypass switch is installed